Application of Constrained Nonlinear Minimization to Estimate Parameters of Transmission Line in Power System Kumkratug Prechanon prechanon@eng.src.ku.ac.th Department of Electrical Engineering, Faculty of Engineering , Kasetsart University at Sriracha Campus, Thailand, 20230 Thailand 27 02 2022

Application of Constrained Nonlinear Minimization to Estimate Parameters of Transmission Line in Power System

Prechanon   Kumkratug

Department of Electrical Engineering, Faculty of Engineering

Kasetsart University at Sriracha Campus

Thailand, 20230

 Article Info ABSTRACT Article history:Received Mar 15, 2022Revised Apr 22, 2022Accepted May 13, 2022 One of the essential components of power systems is the transmission line. It is used in the power system to transfer electricity energy from generation units to load units. Modern transmission line is a complex interconnected network. The mathematical model of transmission line is in nonlinear equations. This paper applied the constrained nonlinear minimization to estimate parameters of transmission line in power system. The great advantage in this proposed method is that the data of the Phase Measurement Unit (PMU) is not required. The ready data at power substations voltage magnitude(V), active (P) and reactive power (Q) is incorporated into mathematical model to estimate the parameters. The various methods of nonlinear iterative available in MATLAB toolbox such as fsolve, fmin, and fmincon are also compared in this paper. Keywords:Constrained nonlinear Minimization,Power systemTransmission lineMATLAB This is an open access article under the CC BY license. Corresponding Author:Prechanon KumkratugDepartment of Electrical EngineeringFaculty of Engineering, Kasetsart University at Sriracha CampusThailand, 20230E-mail:  prechanon@eng.src.ku.ac.th

The accurate parameters of the transmission line consisting of the series impedance (Z) and the shunt admittance(Y) play are very important data in analysis, designing, planing, operation, and protection of powersystem . The Zand Y are due to the effect of magnetic field and electric fields, respectively. There are two possible ways to access the parameters of the transmission line. The first method uses the commissioning data such as, transmission line type, and arrangement, etc., to calculate the parameters . However, commissioning data may be changed by many factors such as conductor degradation, temperature, sag, length, etc. Then it affects on the accuracy of the parameters. The second approach is the so called estimation method. This method uses the measurable data such as voltage, power, etc., with some iterative numerical methods to estimate parameters as can be seen in many previous researches [3, 4]. Research  applied the state estimation to eliminate inaccuracies and errors of calculation. The effects of temperature and sag of transmission were also considered in algorithm as given in . Most of previous researches required the data from PMU [5–7]. However, the PMU is generally implemented at some important power substations because it is an expensive instrument.

This paper proposes the method of estimating parameters of transmission line without the use of the PMU data. The ready data at power substations voltage magnitude (V), active (P) and reactive power (Q) is incorporated into mathematical model to estimate the parameters. The constrained nonlinear minimization available in MATLAB optimization toolbox is applied in this paper.

This section will provide the mathematical model of transmission line in power system. Figure 1 (a) shows the lumped π model of transmission line equivalent. Each π model consists of the series impedance Z and the shunt admittance Y. After some mathematical manipulation of nonlinear differential equation, the transmissionline equivalent in one π model is represented in Figure 1(b). The Z′ and Y′ are given by 

(1)

(2)

(a)

(b)

(c)

Figure 1. Transmission line equivalent (a) distributed π model (b) with a π model (c) two-port representation

The transmission line equivalent in Figure 1(b) can be represented in two-port network as shown in Figure 1(c). The sending end voltage VS and current IS are given by

(3)

(4)

Here

(5)

(6)

(7)

Expressing the sending end voltage in polar form as and the receiving end voltage as reference, the complex power at sending end SS is written by

(8)

After some mathematical manipulations of (4) and (8), the real (PS) and reactive power (QS) at sending end are given by

(9)

(10)

The complex power at recieving end SR is written by

(11)

Similarly, some mathematical manipulations of (4) and (11), the real (PR) and reactive power (QR) at recieving end are given by

(12)

(13)

It can be seen in (9), (10), (12), and (13) that they are in the nonlinear equations of the parameters of the transmission line (R, X, and B) and measurable data at power substation (VS, δ, VR, PS, QS, PR, and QR). The VS, VR, PS, QS, PR, and QR are typically available at power substation. However, the δ must utilize the PMU which is usually implemented at some important power substation because it is expensive instrument. Thus, this paper proposes the method of access the δ. The general form of four equations in four variables of the above equations written by

(14)

Here

(15)

(16)

Nonlinear function optimization is important method to solving parameter in the objective function (F(x)). The necessary condition to minimize the objective equations written by [9, 10]

(17)

Subject to the inequality constrains

(18)

Figure 2. Window of MATLAB optimization toolbox

This paper applies the MATLAB optimization toolbox to solve the above objective equations. Figure 2 shows the window of the MATLAB optimization toolbox . It may be mentioned here that normalization techniques called per unit power system will reduce the effects of the variation in the scale of the solution. In the practical power system industry, the lower xmin and upper xmax bounds in the range between 0 and 1. The initial point x0 may come from the historical data of transmission line implementation. The proposed method is tested on an example to validate the concept involved. A three-phase, 50 Hz, 220 kV transmission line 340 km long. The transmission line parameters considered as the actual parameters are

Z = 0.04+ j37.7 ΩY=j3.761×10−4siemens

The measurable data at power substation is

PS=147.03 MW QS=111.68 MVAR VS=241.14 kV

PR=144 MWQR=108 MVAR VR=220 kV

Figure 3. Comparisons of various numerical methods

There are many solver types in Optimization Toolbox such as fsolve, fmin, fmincon, ga, etc. In this paper, the fslove, fmin and fmincon are compared. It can be seen from Figure 3 that the parameter estimation using the fmincon with constrained nonlinear minimization provides the best results. With 25 iterations, the value of the objective function is less than 1×10-5 and it is considered as global minimum. Then the estimated parameters are approximately equal to the actual parameters.

INTRODUCTION

MATHEMATICAL MODEL

Application of MATLAB Optimization Toolbox and Verification

CONCLUSION

The parameters of the transmission line may be changed by many factors such as the physical properties of a transmission line, temperature, etc. This paper applied constrained nonlinear minimization available in the MATLAB optimization toolbox for estimating parameters of transmission line in power system. It was found that the fmincon with nonlinear constrained minimization provided the best results. This method allows us to utilize the historical data to faster achieve the desired accuracy. The normalization techniques called per unit power system also help to reduce the effects of the variation in the scale of the solution. The simulation results indicated that the proposed method provides the perfect agreement of estimating parameters of transmission line.

REFERENCES

Y. Liao and M. Kezunovic,"Online optimal transmission line parameter estimation for relaying applications, "IEEE Transaction on Power Delivery, 24(1), pp. 96-102, 2009.

W. D. Stevenson, Elements of power system analysis. McGraw-Hill, Singapore, 1982.

C. Rakpenthai and S. Uatrongjit, "Power system state and transmission line conductor temperature estimation, " IEEE Transactions Power Systems, 32(3), pp. 1818-1827, 2017.

Y. Du and Y. Liao, "Online estimation of power transmission line parameters, temperature and sag," Conference on North American Power Symposium, Boston, pp. 1-4, 2011.

V. Milojevi, S. alija, G. Rietveld, and V. S. Laboratorium, "Utilization of PMU measurements for threephase line parameter estimation in power systems," IEEE Transactions on Instrumentation and Measurement. 67(10), pp. 2453-2462, 2018.

S. V. Unde, and S. S. Dambhare, "Double circuit transmission line parameter estimation using PMU, " Conference on IEEE 6th International Conference on Power Systems, New Delhi, India, pp. 1-4, 2016.

M. Asprou and E. Kyriakides, "Estimation of transmission line parameters using PMU measurements, " Conference on IEEE Power and Energy Society General Meeting, Denver, pp. 1-5, 2015.

H. Saadat, "Power system analysis, " McGraw-Hill, Singapore, 1999.

H. Huang, M. Zhou, S. Zhang, and L. Zhang, "Exploiting the operational flexibility of wind integrated hybrid ac/dc power systems, " IEEE Transactions Power Systems, 36(1), pp. 818-826, 2022.

P. Li, M. Yang, Y. Yu, G. Hao, and M. Li, "Decentralized distributionally robust coordinated dispatch of multiarea power systems considering voltage security, "IEEE Transactions on industry and applications, " 57(4), pp. 3441-3450, 2021.

Mathworks, "Optimization toolbox, " https://www.mathworks.com/help/optim/, 2022.